Tel: +86 -27 -6712 7626
Diesel Generator sets
Diesel engine and parts
Analysis of how to control the temperature of the generator set engine room
July 27, 2022
Diesel generator set room temperature control is very important, although the unit itself has a cooling system, but long continuous operation, or the temperature of the engine room, so you are advised to pay attention to the design of the engine room, the specific treatment is as follows.
1, when the temperature difference between indoor and outdoor air is small and the water is not enough, it is appropriate to use direct evaporative chiller unit to reduce the temperature of the generator room.
2, when the water is sufficient and the water temperature can meet the requirements, it is appropriate to use water-cooled way to reduce the temperature of the generator room.
3, when the temperature difference between indoor and outdoor air is large, it is appropriate to use outdoor air to reduce the temperature of the generator room.
If the mobile power station control room requires ventilation, it should be handled separately according to the following different situations.
1, when the mobile power station and the air-raid basement are integrated, should supply fresh air from the air-raid basement to the power station control room.
2, when the mobile power station is set up independently, the control room should be set up by the diesel power station independent ventilation system to supply fresh air, and should be set up filter ventilation device.
3, the mobile power station storage oil room should be equipped with exhaust devices, exhaust ventilation times should not be less than 5 times per hour, connected to the storage oil room on the exhaust duct should be equipped with 70 ℃ off the fire valve.
Analysis of the Cummins diesel generator gas distribution mechanism failure
Analysis of various classifications of diesel generator sets