Tel: +86 -27 -6712 7626
Diesel Generator sets
Diesel engine and parts
Flood season is approaching, the relevant departments to do a good job early flood emergency diesel generator testing and maintenance work
July 11, 2022
With the time to enter the main flood season, in order to protect the power supply at any time, topbo power reminds the relevant departments to organize personnel to test and maintain the standby emergency diesel generators, with load test run work, etc., while paying close attention to weather changes, at any time according to the city flood control arrangements to open the gates to vacate the warehouse.
China's annual flood time in the south is May to June, the north is July to August, the flood season, China's Yangtze River basin and the Yellow River basin will appear significant heavy rainfall weather, the water level will rise, which will occur some waterlogging disasters. As the time enters the main flood season, in order to guarantee the power supply at any time, TopPower reminds the relevant departments to organize personnel to test and maintain the standby emergency diesel generators and test run with load, etc. at the same time, pay close attention to the weather changes and open the gates and vacate the reservoirs at any time according to the city flood control arrangement.
The role of diesel generators is in the case of conventional power grid outages, the use of standby diesel generator sets for the flood gate control system 24 hours of electricity to provide protection for the gate opening and closing operations, is an important power guarantee for the safety of the flood gates. On the management and maintenance of the flood diesel generator set, the user must do the following.
1, the department management personnel shall be familiar with the basic performance and operation of diesel generators, usually should do routine inspection work, so that when the diesel generator failure can be timely and accurate fault judgment, put forward solutions to shorten the fault resolution time, so that the power equipment as soon as possible to resume normal operation.
2, management personnel shall understand the amount of diesel oil reserves are normal, as well as cooling water, oil level and viscosity, cleanliness is normal.
3, once the flood control diesel generator set into operation, the management should go to the engine room to check whether the unit is running normally, including the instrumentation, water temperature, oil volume, etc., there are no abnormalities. Found abnormalities, timely inspection, determine whether the fault will affect the normal operation of the unit, if it will have a serious impact on the unit shall be shut down for maintenance, timely troubleshooting.
4, flood control diesel generator set switch should normally be placed in the automatic start state, for power outages when power generation operation, shorten the power outage time.
5, usually flood control diesel generator set room should be locked. Without the consent of the department head, non-staff entry is prohibited. This can avoid idle personnel to enter the engine room because of curiosity to change the state of the generator settings such as automatic state to manual or inadvertently touch a valve to change the valve state to bring trouble, even in the utility interruptions affect the operation of equipment.
6, diesel generators at least once a week to do a time of not less than 15 minutes no-load test.
Do a good job in advance of the flood emergency diesel generator testing and maintenance work, to ensure that the flood in extreme circumstances such as power outages, diesel generators can do a start on the sound, power supply smoothly, to ensure the safety of urban floods lay a solid foundation.
Several fault problems and repair methods on diesel generator antifreeze
Backup diesel generators provide you with sufficient power during power outages