Tel: +86 -27 -6712 7626
Diesel Generator sets
Diesel engine and parts
To ensure that the technical condition of the diesel generator set is good, the first start of the new machine must pay attention to these matters!
July 07, 2022
After purchasing the diesel generator set of your choice from the generator manufacturer, a series of measures must be taken before starting the diesel generator operation to ensure the actual technical condition of the set is good. Diesel generator set first start-up use to pay attention to matters related to.
After purchasing the diesel generator set of your choice from the generator manufacturer, a series of measures must be taken before starting the diesel generator operation to ensure that the actual technical condition of the set is good. Diesel generator set for the first time to pay attention to the following matters.
1, plus fuel
According to the use of the required fuel quality level, according to the use of diesel generator sets in the region of the ambient temperature selection of fuel, storage conditions, the newly purchased diesel fuel should be added to the diesel engine in the storage device for more than 24 hours before settling.
2, add oil
Diesel generators are shipped without oil, the first time before starting, from the refueling port to fill the required quality, viscosity level of oil, until the oil surface reaches the upper point of the dipstick scale.
Check method: pull out the oil dipstick, wipe clean with a non-fiber wipe, re-insert the dipstick duct, inserted into the restricted position after pulling out, at which time the oil should reach as far as possible to check the upper scale of a scale, if the oil only reaches the following scale, you must refill the oil through the refueling port.
3、Fuel system bleeding
Fuel system bleeding in general is mainly at the fuel filter, the specific practices are as follows.
-Loosen the fuel filter on the bleeder bolt
-Pump the fuel pump by hand until no bubbles of fuel flow from the loosened bleeder bolt.
-After tightening the bleeder bolt, continue to pump by hand for several times.
4、Test run and check
-Check whether the battery is firmly connected by the line
-Running without load for 10 minutes, pay attention to observe the oil pressure, etc., monitor whether the value is normal, check the diesel engine sealing, whether there is oil seepage and other phenomena
-Check the oil level after 1~2 minutes of stopping (oil level should be between the second line scale, refill if necessary).
-Check the v-belt tension
5, the user in the official use of the generator set before, should be required for 60 hours of trial operation.
The first start-up is a very rigorous operation, generally by the generator manufacturer for commissioning test run, commissioning and acceptance before handing over to the user, so as to ensure the technical status of the unit, but also for the user's safety operation has important significance
Hands-on teaching you the correct disassembly and installation of diesel generator set electronically controlled monoblock pump (a)
Three tips on fuel to get good performance from your backup diesel generator