Tel: +86 -27 -6712 7626
Diesel Generator sets
Diesel engine and parts
How to successfully pass the fire inspection for diesel generator sets in the real estate industry?
May 20, 2022
The fire protection acceptance of diesel generator sets is an essential and very important work content. The fire protection acceptance specification of diesel generators for real estate is based on the needs of fire prevention and fire safety, and has strict requirements on the reliability of diesel generator sets. Users should In accordance with the above specifications, make relevant adjustments to improve the fire protection acceptance, so as to successfully pass the fire protection acceptance and put it into safe use as soon as possible.
The fire protection acceptance of diesel generator sets is an essential and very important work content. As an emergency power supply in the real estate industry, diesel generator sets have very strict fire protection acceptance standards. How can users successfully pass the fire protection acceptance? Below, Dingbo Power will introduce the fire protection acceptance standards for diesel generator sets in the real estate industry.
1. Regulations on the layout of diesel generator rooms:
The diesel generator room can be arranged on the first floor or the basement floor, and shall meet the following requirements:
1. When it is set on the ground floor, try to have one side against the outer wall to facilitate ventilation and smoke exhaust.
2. The machine room should be separated from other parts by partition walls and floor slabs that meet the requirements of fire resistance.
3. The computer room is as close as possible to the substation, which can shorten the cable length, facilitate wiring and reduce power loss.
4. Adopt independent fire separation and separate fire compartments.
5. The machine room should be set up as far as possible in a position that is convenient for the hoisting and maintenance of the unit.
Second, the configuration of fire protection implementation:
1. Oil fire extinguishers, dry powder fire extinguishers and gas fire extinguishers must be installed in the machine room.
2. There are fire hydrants, fire hoses and fire water guns outside the machine room.
3. There are emergency instructions and emergency lighting inside the machine room. If the basement is used as the machine room, an independent ventilation system and fire alarm device should be set up.
4. Dry fire-fighting sand is provided inside the machine room.
5. There must be isolation facilities from the oil depot.
6. The generator set should be at least 1 meter away from buildings and other equipment, and the ice should be well ventilated.
7. Set up eye-catching no fireworks icons and no fireworks texts around the computer room.
The fire protection acceptance specification of diesel generators for real estate is based on the needs of fire prevention and fire safety, and has strict requirements on the reliability of diesel generator sets. Users should make relevant adjustments to improve the fire protection acceptance according to the above specifications, so as to pass the fire protection acceptance smoothly. Put into safe use.
Why are diesel generator sets getting more expensive in 2021?
Briefly describe the reasons and harms of diesel generator set's load-carrying capacity decline