Tel: +86 -27 -6712 7626
Diesel Generator sets
Diesel engine and parts
Several factors that need to be considered when designing containerized diesel engine sets
July 12, 2022
Container type diesel generator set is the whole diesel generator line installed in the square cabin, mainly designed and manufactured specifically for the field construction of power supply, the general power in 500kw or more, due to the container type generator set covers an area of small, the container space is also small, need to be reasonable arrangement of vertical and horizontal surface.
Diesel generator sets can be classified into basic diesel generator sets, silent diesel generator sets, mobile trailer type units and container type diesel generator sets according to the appearance and structure, etc. The container type diesel generator set is a whole diesel generator line installed in the square cabin, mainly designed and manufactured for the field construction power supply, the general power is more than 500kw, because the container type generator set covers an area of small The space inside the container is also small, need to be reasonably arranged longitudinally and horizontally, so in the design need to focus on the following factors.
1, containerized diesel generator set as a power supply equipment, the first thing to consider the power output, what type of cable selection, and the way out of the line is how. In addition to diesel generator sets in the container there are other low-voltage supporting equipment, designers must be clear when starting to design the type of these devices, power supply needs, etc.. Set aside in advance the utility capacity and power interface, as well as the control cable interface.
2, often in order to reduce the overall container noise level, while doing more and better protection for the container, container noise reduction box size to do more large, the permeability will be reduced. The consequence of doing so is to affect the ventilation and heat dissipation of the entire unit. Therefore, the container type diesel hair design must account for the entire container into and out of the wind resistance, to avoid exceeding the diesel generator set cooling system limits.
3, in general, the container will be set up a day tank, the capacity of the day tank need not be bound to like installed in the indoor diesel generator set day tank 1m³ limit, container diesel generator set equipment inside the day tank capacity can be made slightly larger, and the day tank needs to drain sewage, the design needs to consider the day tank operation and maintenance space, and to ensure that the day tank exhaust hole led to Outdoor safety parts.
4, focus on the container type diesel generator set of some protective considerations. In the southern region focus on the rain, the north in addition to rain but also consider the willow, snow, cold, warmth. For fire-fighting system, used in the container internal fire-fighting system usually uses heptafluoropropane fire extinguishing system, fire-fighting system is often also linked with the fuel supply system, when the fire alarm, while the day tank of fuel quickly discharge, to avoid further spread of fire.
5, the generator set water jacket water heater, moisture repellent heater, mains charger, box lighting Yun need to configure external power supply, so the low-voltage distribution box is a container-type generator set must be configured. Low-voltage distribution box is usually operated when the unit is stopped, the container design needs to consider the installation and operation of the distribution box space.
6, the generator out of the box to be installed output cable or bus bar, so the generator out of the box needs to be reserved for adequate installation and maintenance space. Or in the corresponding location reserved for operation doors and windows.
What special requirements should diesel generators for fishing boats have?
The large accumulation of carbon will affect the service life of diesel generator sets, how often to clean the carbon?